What You Need to Do
Refer to: National Fire Protection Association [NFPA], ® NFPA 110 Standard for Emergency and Standby Power Systems, 2010 Edition
Look at the survey checklist!
Set up a routine maintenance and testing schedule. (*NFPA 110 8.3.3)
Keep good written records of all inspections, tests, repairs, and maintenance. (*NFPA 110 8.3.4)
Test entire system for 30 minutes after any repair or service. (*NFPA 184.108.40.206)
Run diesel generators at 30% of its rated load for minimum of 30 minutes.
Gas generators need not reach 30% load but must be tested for 30 minutes per month. (NFPA 110 8.4.2 & 220.127.116.11)
Record oil pressure, engine temperature, and AC amperage.
Transfer all transfer switches to the Generator. Include the fire pump transfer switch. (NFPA 110 18.104.22.168 & *NFPA 25 22.214.171.124)
Test the generator and fire pump together at full load. (*NFPA 25 126.96.36.199)
Operate the generator breaker. *(NFPA 110 8.4.7)
Test diesel fuel annually. (*NFPA 110 8.3.8)
Loadbank Test Diesel Only
All information expressed by Standby Power Solutions, LLC or its officers is strictly the opinion of Standby Power Solutions, LLC.
Standby Power Solutions, LLC disclaims any liability for any personal injury, property, or other damages of any nature whatsoever, whether special, indirect, consequential, or compensatory directly or indirectly resulting from the publication, use of, or reliance on this website or any information derived thereof. Standby Power Solutions, LLC also makes no guaranty or warranty as to the accuracy or completeness of any information contained herein. Anyone using this website should rely on his or her own independent judgment, or as appropriate, seek the advice of a competent professional in determining the exercise of reasonable care in any given circumstances. ©2021 by Standby Power Solutions, LLC. All rights reserved. Do not reproduce without express written permission.