A dual fuel gas system for a natural gas emergency generator is not a requirement. It is an option. An onsite fuel supply is the requirement. Natural gas may be used if automatic change-over to an alternate on-site fuel system is provided.
Although we think of natural gas as reliable, it is poor fuel for an engine on a backup (or emergency) generator. NG is subject to contamination, loss of pressure, and interruption. A gas burner may tolerate these issues, while an engine is more demanding and may not operate at all if the NG supply is less than perfect.
For a better explanation view the video.
Also follow us here:
All information expressed by Standby Power Solutions, LLC or its officers is strictly the opinion of Standby Power Solutions, LLC.
Standby Power Solutions, LLC disclaims any liability for any personal injury, property, or other damages of any nature whatsoever, whether special, indirect, consequential, or compensatory directly or indirectly resulting from the publication, use of, or reliance on this website or any information derived thereof. Standby Power Solutions, LLC also makes no guaranty or warranty as to the accuracy or completeness of any information contained herein. Anyone using this website should rely on his or her own independent judgment, or as appropriate, seek the advice of a competent professional in determining the exercise of reasonable care in any given circumstances. ©2021 by Standby Power Solutions, LLC. All rights reserved. Do not reproduce without express written permission.